Aluminum and Glass Rated Doors
We repair all types of fireproof doors and door mechanisms–including pivots, hinges, frames, and closers–in a timely manner.
Glass Fire Rated Doors
The best fireproof door repair services at the fairest prices, and most importantly with great service.
Door Repair NYC provides its services in Manhattan, Brooklyn, Queens, and the Bronx, as well as all across Long Island.
Commercial Fire Rated Doors
A fire door is a door with a fire-resistance rating.
The door is used as part of a passive fire protection system to reduce the spread of fire and smoke.
At Door Repair NYC, we take pride in providing you with the latest products and installation methods, and above all prompt and reliable services. As such, we guarantee superior results and satisfaction.
Our first priority is your utmost satisfaction.
Call For a Quote:
Fire Rated Door
- Aluminum Fire Door
- Fire Rated Entry Door
- Fire-Rated Glass Doors
Fire-rated glass doors are the perfect solution for offices, conference rooms, and lobbies where a fire door is required by code but a glass door is desired for aesthetics.
- Stile & Rail
- Interlocking wood edges
- Keyed-edge hardwood
New Door Installation
Before and After Pictures (In this specipic job, a new staircase was installed).
Can a new door fit the existing frame?
These doors can be provided in a range of sizes to suit most applications, therefore, can be retrofitted to replace existing door sets.
High-Security Fire Doors
Most importantly fire doors must stay closed in the event of a fire. As such properly operating fire door is a key component to stop the spread of deadly fire, smoke, and toxic fumes and gases.
Fire rated doors that are used on a day-to-day basis increase the possibility of a fire door not being in an optimal condition. Therefore, keeping these doors under regular maintenance is very important, inspection is also required.
Laches & Locks
An automatic latching mechanism must be included on an automatic latching mechanism. All hardware needed to be fire listed for instance push bar exit devices, lever handles, and doorknobs.
Fire rated double doors required a listed flush bolt on the inactive leaf or fire vertical exit devices on both leaves.
Life Safety Code
Fire-rated doors are an integral part of a building’s overall fire protection. As a result, fireproof doors are suitable to use throughout design, specification, and installation of rated openings, and most importantly including the language of the Life Safety Code, NFPA 80 and the International Building Code.
Range Of Sizes
The fireproof doors can be provided in a range of sizes to suit most applications, therefore, can be retrofitted to replace existing door sets and opening.
Fire Rated Door Closers
Closer-Holders help stop the spread of fire by closing fire and smoke rated doors when power is interrupted by a fire alarm condition or remote release switch. Hinges with steel bearings or door closers are required at all fire rated openings since fire-rated doors must remain closed at all times (which entails a self-closing mechanism).
Fire Rated Door Panic Device
Fire Exit Hardware is an exit device that is tested for both panic and fire conditions. This device must be used on fire doors where panic hardware is required by code or is desired for durability and safety.
Additional Information Regarding Fire Rated Door Panic Devices
Since fire doors require positive-latching, fire exit hardware does not incorporate mechanical dogging. If a push/pull function is desired for a fire door, electric latch retraction hardware may be installed, as long as the latch projects automatically upon fire alarm.
Fire Alarm Automatic Door Release
Maintain the safety and security of your establishment by installing exit door emergency alarm and lock. This alarm will work with left- or right-handed doors and includes a cover lock to protect the alarm from being disabled. Furthermore, the lock prevents unauthorized entry into your building from the outside, and the bolt assembly is saw-resistant to deter tampering.
A highly visible red sign indicates the location of the emergency exit, and a high decibel alarm is activated when the exit door is opened from the inside. For convenience, the alarm does not need to be hardwired and runs on the included 9V battery. Protect your business, staff, and guests by installing an exit door alarm. Cylinder locks are required to enable door lock and to arm or disarm the alarm.
- Fire doors are rated for three-fourths of the rating of the surrounding wall, for example, A 3-hour door is used in a 4-hour rated wall; a 1/2-hour fire door is used in a 2-hour rated wall, and a 3/4-hour door is used in a one-hour rated wall. But one exception, that 1/3-hour rated doors are also used with one-hour rated walls.
- However, a door with a higher fire rating that opening requires may also be used. For example, a door rated for 3 hours may be used in a 1-1/2 hour opening. In addition, all requirements for the 3-hour rating, such as what is the maximum glass size, door size and other restrictions for the higher rated door must be met.
- For code requirements & standard in NYC, visit the NYC Fire Department’s Website.
- APARTMENT DOORS
- BASEMENT DOORS
- FIRE EXIT DOORS
- HALLWAY DOORS
- COMPACTOR ROOM DOORS
- TANK ROOM DOORS
- GARBAGE ROOM DOORS
- HOSPITAL DOORS
- NURSING HOME DOORS
- LAUNDRY ROOM DOORS
- RESTAURANT DOORS
- CHURCH DOORS
- HOTEL DOORS
- FIRE RATED ACCESS DOORS
- REVERSE SWING DOORS
- BOILER ROOM DOORS
- STAIRWELL DOORS
- BUILDING ENTRANCE DOORS
- ELEVATOR MOTOR ROOM DOORS
- TERRACE DOORS
- LOBBY DOORS
- PACKAGE ROOM DOORS
- SERVICE ENTRANCE DOORS
- PANIC EXIT DOORS
- SIDE ENTRANCE DOORS
According to NFPA 80, Section 126.96.36.199, “As a minimum, the following items shall be verified:”
- No open holes or breaks exist in surfaces of either the door or frame.
- Glazing, vision light frames & glazing beads are intact and securely fastened in place, if so equipped.
- The door, frame, hinges, hardware, and noncombustible threshold are secured, aligned, and in working order with no visible signs of damage.
- No parts are missing or broken.
- Door clearances at the door edge of the door frame, on the pull side of the door, do not exceed clearances listed in 4.8.4 (the clearance under the bottom of the door shall be a maximum of 3/4″) and 6.3.1 (top & edges 1/8″).
- The self‐closing device is operational; that is, the active door completely closes when operated from the full open position.
- If a coordinator is installed, the inactive leaf closes before the active leaf.
- Latching hardware operates and secures the door when it is in the closed position.
- Auxiliary hardware items that interfere or prohibit operation are not installed on the door or frame.
- No field modifications to the door assembly have been performed that void the label.
- Gasketing and edge seals, where required, are inspected to verify their presence and integrity.
Your fire doors must be tested every year (as required by the NFPA) to remain in compliance and optimize safety. Don’t wait for an accident or safety issue to arise. Ensure that your facility’s fire doors work properly by verifying that all of the above-mentioned items are inspected and repaired if necessary.
Manhattan, New York
Our office is open from 8 AM to 8 PM. However, given that our diverse customer base requires a wide-range of working hours, we have adopted a flexible operating model and are available to receive calls at any time! We are proud to be the best, not only in terms of technical aptitude but also in providing the highest quality service in NYC. Your satisfaction is guaranteed.